Breakdown of HVAC points
CI-2009 EAc1.3: Optimize energy performance - HVAC
posted by Chilufya Lombe on Jan 7, 2015, 1:29 pm
Hi, for the HVAC Equipment points (5), our project meets the requirements of sections 1.4 and 2.9 of the core performance guide but not 3.10 since the system is constant volume (as most VRF and...
Last reply: Chilufya Lombe, Jan 12, 2015, 3:10 am
Ice-cream factory with sub-zero working conditions
NC-2009 IEQc7.1: Thermal comfort - design
posted by André Harms on Oct 24, 2014, 10:18 am
The project I'm working on is an ice-cream factory which will have staff working for short spells (but more than 15min) in spaces cooled to down to -40C. This is obviously...
Last reply: Christopher Schaffner, Dec 19, 2014, 3:09 pm
Car Park Ventilation Fan Energy Savings
NC-2009 EAc1: Optimize Energy Performance
posted by Chilufya Lombe on Nov 20, 2014, 8:10 am
Hi, on a recent project we were requested to provide evidence that 5 buildings built within the last three years did not have carbon monoxide sensors installed in the basement car parks in order...
Last reply: Marcus Sheffer, Nov 20, 2014, 10:35 am
Occupancy sensors: No override switch but with task lighting
NC-2009 IEQc6.1: Controllability of systems - lighting
posted by André Harms on Nov 3, 2014, 2:41 am
There are several spaces in a project I'm working on that have been designed with an occupancy sensor without an override switch but each individual work station does have controllable...
Last reply: Larissa Oaks, Nov 6, 2014, 11:26 am