Reference Guide states under Data Center heading: IT energy consumption, as measured from an uninterruptible power supply (UPS) output meter, should be metered separately from non-IT equipment, such as HVAC, plug loads, and lighting. If the UPS system supports non-IT loads that amount to more than 10% of its load, such as lighting or cooling, this non-IT load should also be submetered.
1. For a Non-Data Center building, is total building space cooling end use the sum of IT Room space cooling and Non-IT Room space cooling (remaining building spaces) or is IT Room space cooling considered a separate end use?
2. If IT Room space cooling is a separate end use, then energy model should reflect as individual end use, correct?