To provide workspaces and classrooms that promote occupants’ well-being, productivity, and communications through effective acoustic design.
HVAC Background noise
Achieve a background noise level of 35 dBA or less from heating, ventilating, and air-conditioning (HVAC) systems in classrooms and other core learning spaces. Follow the recommended methodologies and best practices for mechanical system noise control in ANSI Standard S12.60–2010, Part 1, Annex A.1; the 2015 ASHRAE Handbook—HVAC Applications, Chapter 48, Sound and Vibration Control, with errata; AHRI Standard 885–2008; or a local equivalent.
Design classrooms and other core learning spaces to meet the sound transmission class (STC) requirements of ANSI S12.60–2010 Part 1, or a local equivalent. Exterior windows must have an STC rating of at least 35, unless outdoor and indoor noise levels can be verified to justify a lower rating.