The applicant proposes an alternate approach to the enhanced refrigerant impact credit which allows credit for the portion of cooling that is provided by systems that contain no refrigerants.
It is acceptable for the applicant to document that the refrigerant impact for the project (including downstream and upstream systems) is less than a refrigerant impact allowance calculated based on the Baseline cooling capacity* from the EAp2: Minimum Energy Performance Baseline energy model. However, the allowance calculated based on the cooling capacity shall be limited to 75 per ton (versus 100 per ton allowed using the compliance path defined in the Rating System Language for Proposed equipment).
To calculate the Baseline case allowance, multiply the total Baseline cooling capacity from the EAp2: Minimum Energy Performance model by a refrigerant impact of 75 per ton (in this case 483.9 x 75 = 36,292).
To calculate the Proposed case refrigerant impact, complete the EAc4: Refrigerant Impact form for the proposed systems (including upstream and on-site equipment). [Note: for upstream equipment, enter the capacity of the upstream equipment by multiplying the equipment capacity by the proportion of building loads to total district energy cooling loads. For example, if the building loads represent 10% of the district energy cooling loads, multiply the capacity of each piece of upstream equipment by 10%].
If the total refrigerant impact for the proposed design (including upstream systems) is less than the Baseline refrigerant impact allowance identified above, the project shall be deemed to comply with this alternative compliance path.
If using this path, please ensure that energy simulation output files showing both the Baseline cooling and refrigeration capacities AND the Baseline cooling and refrigeration peak operating capacities are uploaded either in EAp2: Minimum Energy Performance or in this credit.
* For the purposes of this Alternative Refrigerant Impact calculation, all uncooled spaces must be excluded from the total Baseline cooling capacity reported unless the documentation demonstrates how passive cooling has been achieved for these spaces.